|Pipe Wall Thickness:
|Cement / Polyurethane
|100% Water Pressure Test
|Yield (≥ MPa):
en545 ductile iron pipe,
PU coatings Ductile Iron Pipe Anti Rust 100% Water Pressure Test overview:
PU Ductile Iron Pipe is ductile iron pipe with a polyurethane coating, polyurethane coating is made of bi-component polyurethane materials to a scale, and not only does it serve as the inner-lining material of nodular castiron pipe, but as related outer errosion resistant coating. Polyurethane coating has many advantages such as wonderful abrasive resistance, excellent corrosion resistance, non-permeation, smmoth surface, small resistance coeffecient, few volatile organic compound,remarkable environmental protection property, ect. Some polyurethane coatings with a thickness of 900μm,are mainly applied to transportingcorrosive mediums or the mediums with high sanitary condition, including soft water, desalination seawater, municipal wastewater, industrial wastewater, and others; and some with thickness above 700μm are mainly applied to the soil environment with strong corrosivity such as the soil polluted by industrial wastewater or with low specific resistance.
Ductile cast iron is kind of alloy of iron, carbon and silicon, in which graphite exists in the type of spherical, generally the size of graphite is 6-7 class, and spheriodization grade of the pipe should be controlled 1-3 class(spheroidization rate is not below 80%). Thus after spheroidization, ductile cast iron possesses the nature of iron as well as the characteristic of steel. After annealing, its microstructure contains ferrite and a little pearlite possessing excellent mechanical properties.Much of the production of ductile iron is in the form of ductile cast iron pipe, used for water and sewer lines. Ductile cast iron pipe is stronger and easier to tap, requires less support and provides greater flow area compared with pipes made from other materials like PVC, concrete, polyethylene or steel. Ductile Iron Pipe is the most widely-used pipeline product in water supply and water drain/sewage projects.
The pipe shall be heated to a temperature within the tolerances recommended by the coating material provider or manufacturer.
The coating shall be applied to the full length of each pipe:
During the coating and curing periods, the coated pipe shall be handled with due care in order to avoid any damage to the coating.
After coating cure, the pipe shall be cooled to facilitate the inspection.
Repairs within the plant are acceptable. They are made under the manufacturer's responsibility. The manufacturer shall select the method and process to be used and establish a written repair procedure.
All coating materials purchased or used under this specification shall be packaged in suitable and approved containers. These containers shall be plainly marked with the name of the manufacturer, type of material and batch or lot number where applicable. Bulk shipment may be allowed provided the above information is included in the bill of loading.
The coating materials shall be packaged in containers suitable to keep the contents clean and dry during handling, shipping and storage. Storage and handling conditions shall be in accordance with the manufacturer's written recommendations.
Precautions shall be taken during handling, shipping and storage of all materials to prevent damage to the containers that would result in contamination of the coating materials. All contaminated or otherwise damaged materials shall be discarded.
The polyurethane used shall be a solvent free two-component system.
Polyurethane, mineral fillers, pigments and additives shall be selected in order that the final product complies with the performance requirements given in clause 6 of this standard.
3. Epoxy resin:
Depending on the method of application, the epoxy resin used shall be:
solvent free two-component liquid, for spray application;
Mineral fillers, pigments and additives shall be selected in order that the final product complies with the performance requirements given in clause 6 of this standard.
4. Performance test DN grouping:
In order to ensure their fitness for purpose in the field of heavy-duty corrosion protection, all the pipes shall fulfil the technical requirements of clause 5 and performance requirements of clause 6.
In order to demonstrate this, the performance tests of clause 6 shall be performed on at least one DN for each of the groupings given in Table A.3. One DN is representative of a grouping when the performances are based on the same design parameters and coating process throughout the size range. If a grouping covers products of different designs and/or manufactured by different processes, the grouping shall be sub-divided. If for a manufacturer a grouping contains only one DN, this DN may be considered as part of the adjacent grouping provided that it is of identical design and manufactured by the same process.
|40 to 500
|600 to 2 000
|Preferred DN in each grouping
Packing: bundled with steel belts or in bulk
Shipment: in bulk or container
Much of the production of ductile iron is in the form of ductile cast iron pipe, used for water and sewer lines. Ductile cast iron pipe is stronger and easier to tap, requires less support and provides greater flow area compared with pipes made from other materials like PVC, concrete, polyethylene or steel. Ductile Iron Pipe is the most widely-used pipeline product in water supply and water drain/sewage projects.
There are lots of qualified managers and technicians, and a well-trained team of after-sales service, which provides all services of manufacture, package, transportation and installation. We are looking forward to cooperating with friends from abroad and home creating a brighter future.